Household & Commercial Water Purifier
Filtration Media & Chemicals
Pump & Blower
Membrane Material: Composite Polyamide
Membrane Type Design: ORM33K Spiral wound
Features: Fiberglass shell (-C) or shrink film-wrapped (-F)
Test Conditions: test solution of NaCl 500 mg/l, P=0,69 MPa, T=25°C , pH=7,5. Recovery – 15%
Nominal rejection is reached after 48 hours of continuous operation on test solution.
Minimal rejection of a new element after 20 minutes test on test solution.
Operating conditions and technical data for designing:
During continuous work with pH over 10,5 the temperature must not exceed 35°С 2) Flow of each element in a batch may vary +/-15% *In case of chemical cleaning with a solution pH exceeding 11,5 or at the temperature level more than 45°С please contact original manufacturer for consultation.
Login To Leave Review
Green Dot Limited offer wide range of first-rate Reverse Osmosis Membrane for Sea Water Treatment Purpose. We focus on h...
FRP Vessel in Bangladesh: Now a days FRP Vessel is utmost popular in Water Treatment Plant in Bangladesh. Fiberglass Rei...